It is basically a load test using resistive load banks to simulate the real potential of this emergency diesel generator at the oil platform during power outage. At first, everything went well up to 100% of rated load and then went astray when trying to reach to 110% load. The SGPS team suggested that the bad quality fuel was the culprit. This is because, during the unofficial FAT, the genset can cope with 110% load for one hour with problem with the previous batch of diesel.
So, the highest we can achieve that day is 108%. The delivery is scheduled on Sunday and the problem can be rectified when the good quality diesel is available.